This website has been archived and is no longer being maintained. The new SSB web site is available from the CERN Service Portal, at: http://cern.ch/ssb
Following a transparent maintenance on a power feed at SafeHost, some servers lost power and went down for an unknown reason.
Expert at CERN and SafeHost are looking at the problem.
Some servers were powered off due to an overload of the PDU installed in the rack when one PDU was stopped during the maintenance.
We are looking at possible solution to avoid the problem in the future.